Yes, the nPP16 can be powered using 208/240VAC. Wire Phase A to the orange wire and phase B to the white wire. The black wire will be capped, and the blue wires will be used to switch the load. Please note:
- Only one of the phases is actually switching on/off – the other phase will remain hot.
- Since the unit is being powered with 220VAC instead of 277VAC, it will provide significantly less bus power.