When using the HOA switch some of the relays do not override on when the switch is set in the on position. The Green indicator lights are off when they should come on and the relay itself is open. When the HOA switch is then set to the off position the relays close and the green indicator lights turn on.
The relay is set to an INVERTED type. To fix this:
1. Start > Programming > Outputs > Relay navigate to the relay or relays in question and check the type. They will read out Inverted*. Press the button next to type and then press the “-“ button to change the type to normal. Press enter. The type will then read out Normal*. The relay will then change back to the normal operational state so that it follows the HOA switch correctly.